Guru installed its technology at the point of generation and across the network in individual properties. This gave Network Homes real-time data on how its network was functioning for the first time.
Data collected by Guru uncovered network losses of 3,350kWh per dwelling per year. Using its machine learning algorithms, Guru Pinpoint helped to diagnose that the Heat Interface Units on site had not been commissioned properly and were performing poorly, resulting in high return temperatures.
The data collected also inspired site investigations which found missing insulation on pipework into dwellings.
With this information, Network Homes replaced faulty valves, insulated pipework within dwellings, and recommissioned and insulated the Heat Interface Units.